0116 4300 272
firstname.lastname@example.org Henley Road, Leicester, LE3 9RD
8.30am to 6.30pm Monday to Friday
RICS Home Surveys Information Sheet - Homebuyers Surveys - Homebuyers Survey Fees - Building/ Structural Surveys
Former shops dating from about 1900
Woodworm infested timbers in an un-ventilated cellar. Lack of ventilation has encouraged dampness and caused extensive beetle infestation. The timber has also formed cubes probably indicative of dry rot decay although no spores were apparent. Note the condensation mould on the ceiling.
The floor bounces when walked on as the spacing of the joists is too wide, the spans too long and they have no criss cross (herring bone) struts to stop the floor twisting.
Damp in a chimney breast probably due to condensation but diagnosis can be difficult. Damp in chimney breasts often allows contaminates to migrate from within the flue. The plaster is best removed and replaced with a sand and cement render to contain the contaminates. A vent appears to have been installed to try and keep one of the flues dry.
The white mould has formed on timbers damp with condensation. The solution is to provide additional ventilation to the roof.
Leicester Office: 51 Henley Road, Leicester, LE3 9RD Derby Office: 34 Queen Street Derby DE1 3DS Coventry Office: The Apex, 2 Sheriffs Orchard, Coventry CV1 3PP Birmingham Office: 22 High Street Sutton Coldfield Birmingham B72 1UX Notingham Office: Courtyard Business Centre, 41a Southwold Drive, Nottingham NG8 1PA Sheffield Office: 16 High Street, Sheffield, S43 3UX